NUVIS Reverse Osmosis Drinking Water System
Delicious, sparkling-clear, drinking water.
Pristine, ﬂavorful coffees, teas, & juices.
Crystalline, harder, and clearer ice cubes.
Save your money! Stop purchasing wasteful bottled water.
The Nuvis Reverse Osmosis System has Five HIGH PERFORMANCE Filtration Stages
Sediment & Activated Carbon Block Module
Protects the automatic shut-off from clogging with microscopic debris, and where the chlorine is removed to protect the refined Composite Membrane.
Reverse Osmosis Chamber
This is the heart of the system. Particles too small to be trapped by the prefilters are removed by the Composite Membrane, further reducing contaminants.
Granular Activated Carbon
Extended contact Granular Activated Carbon further enhances your waters taste and color.
In-line Polishing Filter
The final stage of filtration, an In-line Polishing Filter, removes any remaining tastes and odors before the water reaches it’s final destination; your drinking glass.
Exclusive Patented Manifold Channel Design reduces tubing connections and streamlines installation.
Space-saving design is ideal for under-the-sink installations.
High Capacity TANK
Holds approximately three gallons of water without taking up a lot of space.
High Performance Membrane, with a rating of 50 gallons (189 liters) per day out-put.
Technical Support Information
|Prefilter||Sediment /Activated Carbon Block Module|
|Membrane||Thin Film Composite Module|
|Extended Contact Filter||GAC Module|
|Post Filter||In-Line Carbon Module|
Filter Module Components
|Membrane Production||41 – 53 gallons per day|
|Membrane TDS Reduction||96% Minimum|
|System Production||14 gallons per day|
|System TDS Reduction||93% Average|
Incoming Water Specifications
|Water Pressure||40-100 psig|
|Total Dissolved Solids TDS||2000 ppm maximum|
|pH||4-11 (optimum rejection at pH 7.0 – 7.5)|
|Hardness||Less than 10 gpg or conditioner softened|
|Iron||Less than 0.1 ppm|
|Manganese||Less than 0.05 ppm|
|Chlorine2||See note below|
|Bacteria3||Water source must be potable|
|Temperature||40°F – 100°F|
- Measured at industry standard condition of 65 psig (448 kPa), 77°F (25°C), 600ppm (mg/l) T.D.S., and a discharging to atmosphere.
- Chlorine will damage a T.F.C. Membrane. The Activated Carbine Block Filter will remove chlorine from the incoming water.
Change the cartridge every 12 months; more often if your water contains more than 1 ppm chlorine.
- Do not use with water that is micro-biologically unsafe or of unknown quality, without adequate disinfection before or after the system